APC Back-UPS ES 550 BE550G

http://www.apc.com/resource/include/techspec_index.cfm?base_sku=BE550G&tab=models

http://www.apc.com/products/resource/include/techspec_index.cfm?base_sku=AP9827

Output Output Power Capacity 330 Watts / 550 VA Max Configurable Power 330 Watts / 550 VA Nominal Output Voltage 120V Output Frequency (sync to mains) 50/60 Hz +/- 3 Hz Topology Standby Waveform Type Stepped approximation to a sinewave Output Connections (4) NEMA 5-15R (Battery Backup) 	NEMA 5-15R (4) NEMA 5-15R (Surge Protection) 	NEMA 5-15R Input Nominal Input Voltage 120V Input Frequency 50/60 Hz +/- 3 Hz (auto sensing) Input Connections NEMA 5-15P 	NEMA 5-15P Cord Length 5 feet (1.52 meters) Input voltage range for main operations 88 - 139V Batteries & Runtime Battery Type Maintenance-free sealed Lead-Acid battery with suspended electrolyte : leakproof Typical recharge time 24 hour(s) Replacement Battery APCRBC110 RBC™ Quantity 1 Runtime Graph Hover over the line on the graph above to view the runtime at any desired load This graph is based on actual measured runtime data. All measurements were taken with new, fully charged batteries and a balanced resistive load (PF = 1.0). Actual runtimes may vary from the values of this graph. Actual runtimes are dependent on several variables including battery age, battery charge level, environmental conditions and characteristics of the connected load. View Enlarged Graph View Runtime Chart Energy Use/Efficiency Load 	Efficiency 25% 	97.0% 50% 	98.4% 75% 	98.8% 100% 	99.0% Hover over the line on the graph above to view the efficiency at any desired load Curve fit of data measured in accordance with the ENERGY STAR Program Requirements Product Specification for Uninterruptible Power Supplies (UPSs) - Eligibility Criteria Version 1.0. All measurements taken in normal mode(s), at typical environmental conditions, with 120V/60 Hz electrical input and balanced resistive load (PF = 1.0) output. View Enlarged Graph Communications & Management Interface Port(s) USB Control panel LED status display with On Line : On Battery : Replace Battery and Building Wiring Fault Audible Alarm Alarm when on battery : distinctive low battery alarm : overload continuous tone alarm Surge Protection and Filtering Surge energy rating 340 Joules Filtering Full time multi-pole noise filtering : 5% IEEE surge let-through : zero clamping response time : meets UL 1449 Data Line Protection RJ45 10/100 Base-T Ethernet protection Physical Maximum Height 3.46 inches (88 mm) Maximum Width 7.09 inches (180 mm) Maximum Depth 11.89 inches (302 mm) Net Weight 12.10 lbs. (5.50 kg) Shipping Weight 13.64 lbs. (6.20 kg) Shipping Height 5.04 inches (128 mm) Shipping Width 9.25 inches (235 mm) Shipping Depth 15.47 inches (393 mm) Master Carton Units 2.00 Master Carton Weight 28.60 lbs. (13.00 kg) Color Black SCC Codes 1073130425894 7 Units per Pallet 100.00 5 20 Pallet Weight 1500.00 lbs. (681.82 kg) Environmental Operating Environment 32 - 104 °F (0 - 40 °C) Operating Relative Humidity 5 - 95% Operating Elevation 0–10000 feet (0–3000 meters) Storage Temperature 5 - 113 °F (-15 - 45 °C) Storage Relative Humidity 5 - 95% Storage Elevation 0–50000 feet (0–15000 meters) Audible noise at 1 meter from surface of unit 45.00 dBA Online Thermal Dissipation 16.00 BTU/hr Conformance Regulatory Approvals California (CEC) Battery Charger, ENERGY STAR (USA), FCC Part 15 Class B, FCC Part 68, NOM, TUV-C, UL 1778, UL 497A, UL 497B Standard Warranty 3 years repair or replace Equipment protection policy Lifetime : $75000 Sustainable Offer Status RoHS Compliant REACH REACH: Contains No SVHCs PEP Available in Documentation tab EOLI Available in Documentation tab
 * 1) of Layers per Pallet
 * 1) of Units per Layer per Pallet